IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||5 August 2005|
|PDF File Size:||5.91 Mb|
|ePub File Size:||3.75 Mb|
|Price:||Free* [*Free Regsitration Required]|
BS EN 60099-5:2013
September Replaced By: The requirements iev human safety are not covered by this standard. Surge protective components, current at the date of this publication. TC 37 – Surge arresters rss. The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition.
IEC RLV | IEC Webstore
Computational guide to insulation co-ordination and modeling of electrical networks This technical report gives guidance on conducting insulation co-ordination studies which propose internationally recognized recommendations for the numerical modeling of electrical systems including arresters and for the implementation of deterministic and probabilistic methods adapted to the use of numerical programs.
SS Valve type surge arresters – Terminology. Functional requirements for protective devices are addressed, including varistors and bypass gaps.
This third edition cancels and replaces the second edition published in Related publications IEC Preview Insulation co-ordination – Part 2: The procedures are based on theoretical studies, test results, and experience.
Also includes details of pollutant compositions and methods of application and the procedures associated with 660099-5 mode of pollution.
Contact us svenska Login. Selection and application recommendations Status: These considerations apply specifically to electric utility systems and do not recognize the neutral grounding requirements for dispersed storage and generation. Non-linear resistor type gapped surge arresters for a.
Metal-oxide surge arresters with external series gap EGLA for overhead transmission and distribution lines of a. What is a standard? Surge protective devices, and 37B: Surge arresters – Part 5: When you use our service you can be assured the latest editions and easy access.
Selection and application recommendations. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed. The following test report forms are related: Worldwide Standards We can source any standard from anywhere in the world. Insulation Coordination Standards Insulation co-ordination – Part 1: What makes this amendment so unique is that it is virtually identical to the test procedure published in IEC in A list of standard insulation levels, based on the voltage stress to which the equipment is IEEE C This standard is not maintained and applies to products not manufactured any longer.
Subscribe on standards with our subscription service. Search all products by.
Included are requirements for safety, rating, and protective device levels. It specifies the procedure for the selection of the rated withstand voltages for the phase-to-earth, phase-to-phase and longitudinal insulation of the equipment and the installations of these systems.
You may find similar items within these categories by selecting from the choices below:. Low-voltage limiters are covered under Clause 7. It applies to gapless metal-oxide surge arresters as defined in IECto surge arresters containing both series and parallel gapped structure — rated 52 kV and less as defined in IEC and metal-oxide surge arresters with external series gap for overhead transmission and distribution lines EGLA as defined in IEC Read more about SIS Subscriptions.
Learn more about the cookies we use and how to change your settings. Message to your colleague. Find Similar Items This product falls into the following categories. It also gives the lists of the standard withstand voltages from which the rated withstand voltages should be selected.